By Institute of Electrical & Electronics Engineers
Read or Download IEEE Std 142-1982, IEEE Recommended Practice for Grounding of Industrial and Commercial Power Systems PDF
Best power systems books
Die dritte Auflage dieses Bandes der elektrischen Energietechnik wurde im Kapitel 1 und 14 sowie im Anhang aktualisiert und erganzt. Die ubrigen Kapitel erfuhren nur Anpassungen zur besseren Koordination in Zusammenhang mit der Erweiterung und Aufspaltung des zweiten Bandes des Werkes in zwei Bande im Rahmen der dritten Auflage.
Case reviews up to speed provides a framework to facilitate using complex keep an eye on innovations in genuine structures in response to twenty years of analysis and over a hundred and fifty profitable purposes for commercial end-users from a variety of backgrounds. In successive elements the textual content ways the matter of placing the speculation to paintings from either ends, theoretical and useful.
This booklet examines the explanations why a number of teams around the globe opt for to not undertake broadband providers and evaluates recommendations to stimulate the call for that may bring about elevated broadband use. It introduces readers to some great benefits of larger adoption premiums whereas studying the growth that built and rising international locations have made in stimulating broadband call for.
This moment variation to a favored first offers a finished, totally up-to-date therapy of complicated traditional energy iteration and cogeneration vegetation, in addition to substitute power applied sciences. equipped into elements: traditional strength iteration expertise and Renewable and rising fresh strength platforms, the e-book covers the basics, research, layout, and useful elements of complicated strength structures, therefore offering a robust theoretical history for hugely effective power conversion.
- Elektrische Maschinen und Antriebe: Lehr- und Arbeitsbuch
- J & P Transformer Book
- Civil Engineering Design for Decommissioning of Nuclear Installations
- Voltage-Sourced Converters in Power Systems: Modeling, Control, and Applications
- Dynamic Power Management: Design Techniques and CAD Tools
- Protection of Electricity Distribution Networks, 2nd Edition (IEE Power and Energy Series)
Extra info for IEEE Std 142-1982, IEEE Recommended Practice for Grounding of Industrial and Commercial Power Systems
1977, pp. 92–99. Gustafson, R. , and Albertson, V. D. “Neutral-to-Earth Voltage and Ground Current Effects in Livestock Facilities,” IEEE Transactions, vol. PAS-10, no. 7, July 1982, p. 2090. Kaufmann, R. H. and Page, J. C. “Arcing Fault Protection for Low-Voltage Power Distribution Systems,” AIEE Transactions on Power Apparatus and Systems, vol. 79, June 1960, pp. 160–167. Surbrook, T. , Reese, N. D. and Althouse, J. , “Parameters Affecting Neutral-to-Earth Voltage Along Primary Distribution Circuits,” IEEE Transactions on Industry Applications, vol.
1 Grounded/Grounding Conductor Arrangement. Since the UPS module output neutral is solidly connected to the bypass input (service entrance) neutral, the UPS module is not considered a separately derived system according to the NEC. In this system, (1) the UPS neutral should not be bonded to the equipment grounding conductor, and (2) no local grounding electrode conductor should be installed to the UPS module. 2 Features/Performance. While this arrangement may be typical for 208 V input/208 V output UPS systems, it does not provide any isolation or common mode noise attenuation for sensitive loads.
2 Configuration 2 Single UPS Module, Isolated Bypass. In this configuration (Fig 10), a bypass transformer is used to feed the bypass input of the UPS module. The bypass transformer and UPS module together constitute a separately derived system, since there is no direct electrical connection between the input (service entrance) circuit conductors and the output circuit conductors. 1 Grounded/Grounding Conductor Arrangement. Since this configuration is considered a separately derived source, the neutral of the UPS module should be bonded to the equipment grounding conductor, and a local grounding electrode module should be installed, per NEC , 250-26.